Biological Sewage Treatment Plant
Raw sewage is passed to an aeration chamber and air is supplied through diffusers. This promotes the action of aerobic bacteria which break down the sewage into carbon di oxide, water and inorganic waste. Figure below shows a typical biological sewage treatment plant.
Sewage then passes into the clarification or settling chamber. Any solids that settle out are returned via an air lift to the aeration chamber which ensures that they are fully broken down. The sample applies to any surface scum. A small vane type air compressor supplies the air for air diffusers and air lift.
The clear liquid then passes through the chlorinator where the liquid is disinfected, into the chlorination chamber. The chamber has float switches, which control the discharge pump, and a high level alarm.
Although the sewage treatment plant runs automatically, without regular maintenance the unit will not function properly and anaerobic bacteria may promote the formation of hydrogen sulphide and methane, both of which are hazardous.
The chambers need to be cleaned out occasionally to remove any accumulated matter. The aeration diffusers should be checked to ensure they are clear and that air is bubbling from them. The air lift returns should also be checked to make sure they function correctly. These usually have a clear plastic pipe so that the sludge can be seen returning to the aeration chamber.
The internal tank coating should be inspected for any signs of cracking or blistering.
When cleaning out a sewage unit rubber gloves and a mask should be worn. After overhaul the external surfaces of the unit and surroundings are to be washed down with disinfectant. Hands should also be thoroughly scrubbed and overalls washed.
"Operation and Maintenance of Machinery in Motor Ships" by N.E. Chell
More by this Author
It sometimes necessary to obtain an approximation to the power of the ship without restoring to model experiments, and several methods are available. One system which has been in use for several years is the admiralty...
Shell and Tube, Plate Heat Exchangers Advantages Simple and Compact in size Heat transfer efficiency is more Can be easily cleaned No extra space is required for dismantling Capacity can be increased by...
Linear resistors are those in which current produced is directly proportional to the applied voltage. Their current versus applied voltage is straight and linear. In other words, their resistance remains constant. ...