Transformers lab report
LAB REPORT ELECTRICAL POWER
Open circuit and short circuit tests of a single-phase transformer
1. To study the variation of iron loss and no load current with the applied voltage
2. To determine the equivalent circuit parameters of the single phase transformer
1. (100VA, 240/110) single phase transformer 1 no.
2. (0-250V, AC) voltmeter 1 no.
3. (0-150V, AC) voltmeter 1 no.
4. (0-1A, AC) ammeter 1 no.
5. Wattmeter 1 no.
6. 230/(0-250V) variac 1 no.
7. Leads 8 no.
For a practical transformer the following features should be taken in to account:
1. Finite winding resistance
2. Flux is not entirely confined to the core. Some portion appears as a leakage.
3. It draws a finite current from the source on no load.
4. It contains hysterisis and eddy current losses.
5. The magnetic circuit of the transformer is not linear.
By taking suitable steps, we can separate out those deviations in the practicle transformer and derive some relationship. We will use them to predict the performance of the transformer.
The exact equivalent circuit of a transformer is as shown in Figure 1
R1: Primary winding resistance
R2: Secondary winding resistance
X1: Primary leakage reactance
X2: Secondary leakage reactance
RC: Equivalent resistance to represent Iron loss
Xm: Magnetizing reactance
Part A: Open circuit test
(a) Examine the transformer and note down the rated voltage, KVA rating and operating frequency.
(b) Identify the HV side and LV side and calculate the rated currents for each side.
(c) Connect the circuit as shown in Figure 2.
Note that the open circuit test is done on the LV side while HV side is open circuited.
(d) Keep the variac at it's minimum position.
(e) Switch on the power supply and raise the primary voltage to it's rated voltage.
(f) Note down the ammeter (IOC), voltmeter (VOC) and the wattmeter (WOC) readings.
(g) Decrease the primary voltage in steps of 10V and observe the meter readings on the given table below.
Table of results
Result-1 Plot the wattmeter reading (Iron Loss) vs. applied voltage and applied voltage vs. no Load Current.
VOC Primary input voltage when the secondary is open circuited.
IOC Primary current when the secondary is open circuited.
WOC Iron loss when the secondary is open circuited.
For rated values note down the following observations.
More by this Author
Technical factors affecting economics of electricity supply Contents 1.1 What is an electric power system? some technical considerations 1.1.1 Generation 1.1.2 Transmission ...
Contents 4.1 How do you receive electrical power at your home or office? 4.2 Distribution substations 4.3 Types of distribution systems ...
Introduction to electrical installation and wiring regulations Contents 5.1 Applicable regulations 5.2 Electricity act 5.3 Wiring regulations ...