My central air is blowing warm air in the house and cold air out of my unit outside?
My fan won't start unless I kick start it with a stick, I read about this being a possible bad capasiter. Would this possibly be the cause of the warm air as well even after I get the fan going? Or does this sound like a different problem, possibly low coolant?
First of all, what it sounds like is you've got a heat pump. A heat pump is an air conditioner that has a three way valve allowing for it to reverse the operation - so that it can function as a heater or an air conditioner without using electric heat strips, or a gas furnace.
It will have either electric heat strips or a gas furnace paired with it, but those will not get employed unless the temperature drops enough that it can't keep up with the demand for heat inside the home without their use.
So when the three way valve, also knows as a reversing valve gets stuck - the unit deposits refrigerated air outside in air conditioning mode, and hot air inside.
Did that make sense? You're question describes a heat pump central heating and air unit with a stuck reversing valve.
Now, the thing about your fan motor is another problem entirely. Yes, a run capacitor MIGHT BE needed to fix that problem. But it could also be that your fan motor's bearings are shot, and if that is the case, then the motor itself should be replaced. The person replacing it should always replace the run capacitor along with the motor.
by steven240sx2 years ago
My gas furnace is blowing cold air some of the time. The burner kicks in for about 10 seconds...then kicks off, then the fan starts.(blowing cold air). Some times it works properly, heating longer and keeping the...
by Rhonda D Johnson5 years ago
Am I paying too much for electricity?I live in a large, one bedroom, all electric apartment. Even the hot water heater is electric. My bill has always hovered around $50, but gets outrageous during the...
by Sharon Smith5 years ago
What are the pros and cons of whole house air conditioning vs. window air conditioners?
by Astralrose5 years ago
How does your home heating being done?I always wonder if there's a central heating for every house in America or Europe, places which are almost always cold and how is it being done. Here in the upper/higher region of...
by Melissa Flagg OSC2 years ago
Why does my A/C smell like the heat is on?I checked, it's not, but it smells like the heat is on, it doesn't seem to be blowing much air and it's definitely not cold, just cool. It's ancient, like 20 years old I think....
by yarisgs6 years ago
Car heater blowing cold air when turn on full speedHi I just bought a 2003 TOYOTA YARIS GS 998CC. My problem is this when I turn heater to the warmerst setting and then put on high I only getting cold air but if I have...
Copyright © 2018 HubPages Inc. and respective owners.
Other product and company names shown may be trademarks of their respective owners.
HubPages® is a registered Service Mark of HubPages, Inc.
HubPages and Hubbers (authors) may earn revenue on this page based on affiliate relationships and advertisements with partners including Amazon, Google, and others.