I need guidance to grab power from a mid run existing receptacle to add a bathroom GFCI receptacle
You will need to fish either a 14-2 or a 12-2 wire (the same as in the existing plug) to the new box in the bathroom. You can also determine the correct size from the circuit breaker rating. You will have to locate that particular breaker in any case; a 15 amp breaker can use 14-2 wire (or 12-2) but if it is a 20 amp breaker it will require 12-2 wire. If in doubt, use 12-2 (12 guage, 2 conductor plus ground).
Wires should be simply spliced into the same color wire in the existing box and terminated on the appropriate terminals on the new GFI. Make sure you terminate them on the "line" terminals, not the "load" terminals. Most new GFI plugs have a piece of tape across the "load" terminals but they are marked as well.
The only real problems you might encounter would be actually fishing the wire to the new location or if the existing plug is a GFI itself. If it is the new wire will need to be spliced into the existing wire with wire nuts rather than terminated on the same screws; you cannot put two wires onto one terminal on most GFI plugs.
You should be aware that the existing plug is probably on a 15 amp circuit breaker and this will limit the amount of current available in the bathroom. It will run a hair dryer, but probably not two of them at once.
If this does not answer your question, please either email me from the email listed on my profile or leave a comment on my hub about wiring plugs (http://hubpages.com/hub/how-to-install- … al-outlets). Either way I will get back to you.
by michiganman567 6 years ago
If I change a 15amp circuit breaker to a 30 amp circuit breaker, do I also have to change the wire?I got a new air compressor, but it trips the circuit, so I have to change my breaker. I thought that I would also have to change the wire, but someone told me that I can use the 12 gauge wire...
by billy debig bovoe 7 years ago
bought property and put our 5 wheel camper on it. We had a 100 amp electric service put in. The...guy put a 220 breaker in when I hooked up my trailer the vcr and microwave caught on fire . Now I am plugged in and have the 30 amp 110 breaker in and have no power to anything. I hooked the...
Copyright © 2018 HubPages Inc. and respective owners. Other product and company names shown may be trademarks of their respective owners. HubPages® is a registered Service Mark of HubPages, Inc. HubPages and Hubbers (authors) may earn revenue on this page based on affiliate relationships and advertisements with partners including Amazon, Google, and others.
|HubPages Device ID||This is used to identify particular browsers or devices when the access the service, and is used for security reasons.|
|Login||This is necessary to sign in to the HubPages Service.|
|HubPages Traffic Pixel||This is used to collect data on traffic to articles and other pages on our site. Unless you are signed in to a HubPages account, all personally identifiable information is anonymized.|
|Remarketing Pixels||We may use remarketing pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to advertise the HubPages Service to people that have visited our sites.|
|Conversion Tracking Pixels||We may use conversion tracking pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to identify when an advertisement has successfully resulted in the desired action, such as signing up for the HubPages Service or publishing an article on the HubPages Service.|