If I change a 15amp circuit breaker to a 30 amp circuit breaker, do I also have to change the wire?
I got a new air compressor, but it trips the circuit, so I have to change my breaker. I thought that I would also have to change the wire, but someone told me that I can use the 12 gauge wire that is currently in the wall.
if your home has updated wiring and you aren't living in a house where the wiring is from the turn of the last century and your compressor runs on 110 to 120 not 220-240 then changing to a twenty amp fuze to solve your issue is ok.
But you might want to figure out what else is on that circuit and why the compressor is blowing the 15 amp fuze. It will likely be rated to run at much lower than that, but for some reason when it starts up there is a spike in the amps it draws, thus blowing the fuze. It's a common issue with electric motors.
If the line you are running it on also has the fridge on it, for instance, the combined amps might be too high when both are starting at the same time or one is running and the other starts.
If nothing else is running on the circuit the motor on the compressor may be bad.
Put an amp probe on it when it starts up and see what it is trying to pull. If it is really high you may need a new compressor motor.
But most likely it is a matter of too much on one circuit. I recommend looking in to the following: First find out what is on the circuit. Check what amperage the manufacturer recommends you run it on. Call them if need be, Check the amperage it tries to draw on start up. if below 20 amps switch to a twenty amp fuze or breaker. If above I would start worrying about the motor.
But I would not switch to a thirty amp fuze unless that is what the manufacturer recommends, which is doubtful.
Check your local electrical codes or get a do-it-yourself home wiring book from one of the large home improvement stores. There is a max breaker amperage for a given wire size. Typically the maximum breaker size for 12 guage wire is 20 amps; for 14 gauge wire is 15 amps, etc. A 30 amp breaker is too large for 12 gauge wire and would be unsafe. The presence of 12 gauge wire from a 15 amp breaker is puzzling. Try to check the wiring for this circuit at several points to be sure it is 12 gauge throughout, i.e., that someone has not added a 14 gauge run somewhere and reduced the breaker to keep it safe. It is possible, of course, that the original breaker went bad and someone replaced it with a 15 amp one. When you are checking for possible other things on this circuit, don't forget to consider overhead lights and outside lights as well as outlets.
by Drew Bobbitt 3 years ago
How do you tell amperage of a circuit breaker?I have this breaker and am curious as to wether this is a 30-amp setup, or are they combined to create a 60-amp setup.
by Tina Burnett 15 months ago
My travel trailer a/c has always kept trailer cool. The fan works but a/c won't go on.It has been tripping the breaker that our trailer is connected to. Also the power will drop and I can hear a weird buzzing or motor noise when I'm in rear of trailer by the electrical panel. I can't tell if noise...
by Liz Elias 6 years ago
How do you wire a half-hot outlet?Can such an outlet be fed from an existing wall switch, or would I need to replace the switch with a duplex switch, one for the existing ceiling light and the second for the half-hot? In either case, would I need a "traveler" such as with a 3-way...
Copyright © 2018 HubPages Inc. and respective owners. Other product and company names shown may be trademarks of their respective owners. HubPages® is a registered Service Mark of HubPages, Inc. HubPages and Hubbers (authors) may earn revenue on this page based on affiliate relationships and advertisements with partners including Amazon, Google, and others.
|HubPages Device ID||This is used to identify particular browsers or devices when the access the service, and is used for security reasons.|
|Login||This is necessary to sign in to the HubPages Service.|
|HubPages Traffic Pixel||This is used to collect data on traffic to articles and other pages on our site. Unless you are signed in to a HubPages account, all personally identifiable information is anonymized.|
|Remarketing Pixels||We may use remarketing pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to advertise the HubPages Service to people that have visited our sites.|
|Conversion Tracking Pixels||We may use conversion tracking pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to identify when an advertisement has successfully resulted in the desired action, such as signing up for the HubPages Service or publishing an article on the HubPages Service.|