|HubPages Device ID||This is used to identify particular browsers or devices when the access the service, and is used for security reasons.|
|Login||This is necessary to sign in to the HubPages Service.|
|HubPages Traffic Pixel||This is used to collect data on traffic to articles and other pages on our site. Unless you are signed in to a HubPages account, all personally identifiable information is anonymized.|
|Remarketing Pixels||We may use remarketing pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to advertise the HubPages Service to people that have visited our sites.|
|Conversion Tracking Pixels||We may use conversion tracking pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to identify when an advertisement has successfully resulted in the desired action, such as signing up for the HubPages Service or publishing an article on the HubPages Service.|
How do you tell amperage of a circuit breaker?
I have this breaker and am curious as to wether this is a 30-amp setup, or are they combined to create a 60-amp setup.
US domestic supply systems are split-phase. So homes are supplied with 2 phases or hots and a neutral. Each hot is at a potential of 120 volts with respect to ground. Lower powered appliances are fed from 120 volts, and higher powered appliances are powered by 240 volts which is derived from the voltage between the two hots.
This is a 2 pole common-trip breaker used to supply 240 volt appliances. The inputs to the breaker are fed from 2 different phases or hots. Each of the hots is at a potential of 120 volts with respect to neutral. Either of the output terminals of the breaker can supply 30 amps max to a circuit at 120 volts. That's 30 + 30 = 60 amps total to two separate 120 volts circuits. However this type of breaker is usually used to supply 240 volts circuits (There is 240 volts between the two output terminals) and will supply 30 max to a circuit. The reason the operating handles are joined is so that if one phase sources too much current, the breaker will trip and shut the other breaker off also. This ensures the circuit is totally isolated from both hots. A dangerous scenario can occur if a 240 volt circuit is wired from 2 single breakers. If one of the breakers trips due to an overload (and the other breaker doesn't trip) or if someone turns off a breaker to do maintenance, 120 volts can still be present, presenting a shock hazard.
I hope this is accurate! Maybe our resident electrician, Wilderness, can add to this?
by michiganman5676 years ago
If I change a 15amp circuit breaker to a 30 amp circuit breaker, do I also have to change the wire?I got a new air compressor, but it trips the circuit, so I have to change my breaker. I thought that I would also...
by Truckstop Sally6 years ago
Do you know how a breaker box works? and how to re-set it, if necessary?Ladies -- Be honest! And if not, I challenge you to find out!!I often "throw" a breaker when ironing or running the dishwasher, so...
Copyright © 2018 HubPages Inc. and respective owners.
Other product and company names shown may be trademarks of their respective owners.
HubPages® is a registered Service Mark of HubPages, Inc.
HubPages and Hubbers (authors) may earn revenue on this page based on affiliate relationships and advertisements with partners including Amazon, Google, and others.